Galvanized steel potable water supply and distribution pipes are commonly found with nominal pipe sizes from 3?8 inch (9.5 mm) to 2 inches (51 mm).It is rarely used today for new construction residential plumbing. Steel pipe has National Pipe Thread (NPT) standard tapered male threads, which connect with female tapered threads on elbows, tees, couplers, valves, and other fittings. Galvanized steel (often known simply as "galv" or "iron" in the plumbing trade) is relatively expensive, and difficult to work with due to weight and requirement of a pipe threader.
Plumbing is any system that conveys fluids for a wide range of applications.Heating and cooling, waste removal, and potable water delivery are among the most common uses for plumbing however plumbing's not limited to these applications.1 Plumbing utilizes pipes, valves, plumbing fixtures, tanks, and other apparatuses to convey fluids.2 Trades that work with plumbing such as boilermakers, plumbers, and pipefitters are referred to the plumbing trade.
In the Developed world plumbing infrastructure is critical for public health and sanitation. Źródło: https://en.wikipedia.org/wiki/Plumbing#Systems
The difference between pipes and tubes is simply in the way it is sized. PVC pipe for plumbing applications and galvanized steel pipe for instance, are measured in IPS (iron pipe size). Copper tube, CPVC, PeX and other tubing is measured nominally, which is basically an average diameter..
These sizing schemes allow for universal adaptation of transitional fittings.For instance, 1/2" PeX tubing is the same size as 1/2" copper tubing.
1/2" PVC on the other hand is not the same size as 1/2" tubing, and therefore requires either a threaded male or female adapter to connect them.When used in agricultural irrigation, the singular form "pipe" is often used as a plural.7 Pipe is available in rigid "joints", which come in various lengths depending on the material.
Tubing, in particular copper, comes in rigid hard tempered "joints" or soft tempered (annealed) rolls.
PeX and CPVC tubing also comes in rigid "joints" or flexible rolls.
The temper of the copper, that is whether it is a rigid "joint" or flexible roll, does not affect the sizing.7 The thicknesses of the water pipe and tube walls can vary.Pipe wall thickness is denoted by various schedules or for large bore polyethylene pipe in the UK by the Standard Dimension Ratio (SDR), defined as the ratio of the pipe diameter to its wall thickness. Pipe wall thickness increases with schedule, and is available in schedules 20, 40, 80, and higher in special cases.
The schedule is largely determined by the operating pressure of the system, with higher pressures commanding greater thickness.Copper tubing is available in four wall thicknesses: type DWV (thinnest wall; only allowed as drain pipe per UPC), type 'M' (thin; typically only allowed as drain pipe by IPC code), type 'L' (thicker, standard duty for water lines and water service), and type 'K' (thickest, typically used underground between the main and the meter).Because piping and tubing are commodities, having a greater wall thickness implies higher initial cost.Thicker walled pipe generally implies greater durability and higher pressure tolerances.Źródło: https://en.wikipedia.org/wiki/Water_pipe#Difference_between_pipes_and_tubes